Shelf indoor host pulse cleaning dust collector Dust manufacturers
Warehouse roof ESP The dust separated from the flue gases out of equipment called dust or dust removal equipment. Precipitator performance with the amount of gas that can be processed, expressed through gas pressure loss and collection efficiency of dust during the same time, the price of dust, running and maintenance costs, length of life and ease of operation and management is considered an important factor in the performance of uses: Dust is commonly used in boilers and industrial production facilities precipitator divided into the following five categories according to their action principle; (1) mechanical force. including gravity dust filter, inertial dust collector, centrifugal dust collector and so on.
two, Filter Cleaning method
Once every six months, remove the filter for cleaning.
Once every six Remove filter cleaning.
Cleaning can be compressed air or high-pressure steam (maximum temperature not exceeding
80 0C) ,
Use compressed air or high pressure steam cleaning
(The maximum temperature of over 80 0C).
Were spray-washed the outside of the filter at a distance of 40 cm from the top of the filter slowly
Toward the bottom.
In the filter lateral distance of 40 cm for jet washing.
Gradually shift from the top of the bottom of the filter.
After washing, the filter opening down to the water outflow.
After washing, opening facing down so that water will
Let it stand at room temperature for about a week to dry.
Once dry place at room temperature for about a week.
Or in the oven (maximum temperature not exceeding 80 0C) bake about 20 hours
It can be dry.
Or in the oven (the maximum temperature of over 80
0C) to try to be out of work for about 20 hours.
III. Maintenance Maintenance
Once every three months, check the site clean dust inside
Are there dust appear;
If there is dust, then:
1. Check the filter is broken;
2. Check the sealing parts;
3. Check the filter is properly installed in the mounting plate.
Once every three months to check
whether a dust precipitator internal
parts of the cleanliness there.
1. Check whether the damaged filter;
2. Seal inspection sites;
3. Check whether the correct installation of
the filter installed board