|The amount of wear: 0.1 || Crashworthiness strength: 0.6-2.5 (MPa) || Pipe thickness: 25-300 (mm) |
| Friction coefficient: 0.1 || For fluid: Various petrochemical, pharmaceutical and other industries liquids or gases || Custom processing: |
| Material: carbon steel, stainless steel || Pipe diameter: 25-300 (mm) || Model: XSQ-ZQ |
| Brand: Beijing Jing Chen || Operating temperature range: -40 ~ 60 (℃) |
- Muffler is to prevent sound transmission while allowing air flow through a device, is an important measure to eliminate aerodynamic noise muffler is mounted on the aerodynamic devices (such as blowers, air compressors) airflow passage or intake and exhaust system The noise reduction devices. muffler can stop the propagation of sound waves, to allow air flow through, is an effective tool to control noise. Many types of muffler, but their silencer mechanism, but they can be divided into six main types, namely muffler Resistive muffler, muffler, impedance composite muffler, micro-perforated plate muffler, muffler holes and active muffler.
- Steam muffler installation instructions:
① exhaust muffler should be perpendicular to the factory roof installation, shown in Figure 3, with a steel bracket holder and factory muffler is fixed.
② to increase wind resistance Powerhouse altitude, exhaust muffler body with a support-type bearings, for exhaust muffler exhaust pipe shall be a period of expansion before bend to absorb the thermal expansion, such as the original exhaust pipe hydrophobic plate already installed in the vertical direction, the expansion loops to avoid wear.
③ Exhaust muffler base body are designed with a drainage pipe or weep holes should check the orifice should be smooth.
④ exhaust steam pipe hole piercing the top platform of the plant, there should be a thin steel plate rain cover (Figure 3).
⑤ security door, in principle, a security door with a silencer, safety gates have two single-seat and two-seater, two-seater can be ranked for when you install steam pipes are combined into a single manifold communicating with the muffler, but row a large amount of steam two-seater security door, you can also install two muffler.
⑥ on the Deaerator, shooting steam exhaust and other air ejector for small displacement Exhaust muffler , Into a tubular shape design, installation more convenient. Installation shown in Figure 4. Exhaust muffler Vertically along the main plant walls, columns installed in the wall, the column set steel sliding bracket, muffler and piping erection thereon, muffler exhaust port coping with a roof direction should be noted, have been made when there is this type of muffler factory fixed seat, sliding bracket when mounted, fixed bearing can not. Figure 4.
- Please specify when ordering: Product name, nominal diameter, detailed parameters of the pressure rating, material, flange standards, operating pressure, the media and above the size of conventional general-purpose products, for other size, welcome to call us.