|The amount of wear: 1 || Crashworthiness strength: 0.6-2.5 (MPa) || Pipe thickness: 3-5 (mm) |
| Friction coefficient: 0.1 || For fluid: Various petrochemical, pharmaceutical and other industries liquids or gases || Custom processing: |
| Material: carbon steel, stainless steel, 304 || Pipe diameter: 25-300 (mm) || Model: ZHQ-B ZHQ-1 |
| Brand: Beijing Jing Chen || Operating temperature range: -40 ~ 450 (℃) |
Pipeline (gas) flame arrester Principle is the application of flame through a narrow pore thermal conductor , Principles of design and manufacturing due to heat loss and extinguished suitable for combustible gas pipelines, such as gasoline, kerosene, light diesel oil, benzene, toluene, crude oil and other oil storage and filling or flare system, gas purification Tonghua system, gas analysis systems, coal gas drainage system, furnace fuel gas pipe-line, can also be used in acetylene, oxygen, nitrogen, natural gas pipeline supplies.
Pipeline (gas) flame arrester equipment materials Principle Materials of construction:
Fire retardant core member
Fire retardant box
Bolt / nut
Bolt / Nut
Carbon Steel Casting
Note: Connection Standard: HG, GB, ANSI, JIS, DIN and so on.
Standard Connection: HG, GB, ANSI, JIS, DIN, ect.
Operating pressure: 0.6-5.0Mpa (150Lb-600Lb)
Operating Pressure: 0.6-5.0Mpa (150Lb-600Lb)
Pipeline (gas) flame arrester Principle repair and maintenance:
In order to ensure the safety arrester performance to the intended use of the flame arrester should be checked regularly maintained. Zuhuo inspected once every six months to check fire resistant layer core is blocked, deformation, corrosion was found to be blocked fire resistant layer core should be cleaned to ensure that each of the perforations on the core flow, deformation and corrosion for fire resistant layer should be replaced. reinstall fire resistant layer core, it should not be leak tight to ensure the joint surface.