Softening device is used cation exchange resin to soften water; the main purpose is to allow the cation resin adsorption of calcium in the water; magnesium ions (the main component of the formation of scale), reduce water hardness, and can be resin regeneration, recycling Zhengzhou IndyMac Produced by DM automatic softener is to run every step of softening and regeneration to achieve automatic control, and the use of time, flow or other sensors, etc. to start regeneration automatic softener basically consist of: American fleck or osmonics-autotrol multiple control valve, resin tank (containing resin), salt boxes and piping systems.
DM automatic water softener uses sodium ion exchange resin raw water calcium and magnesium ion substitution out, after the device outflow and for the low hardness demineralized water. When the resin is adsorbed to a certain amount of calcium and magnesium ions after, must be regenerated : with saturated brine resin to resin in the calcium; magnesium ion exchange out again; restore soften exchange capacity of the resin and liquid effluents to the regeneration process includes: backwash - loose resin layer; absorption of salt regeneration - are exchanged reaction; flushing (flushing) - calcium exchange down the chemical reaction, magnesium ions rinse water - for the next regeneration.
1, high degree of automation
DM automatic softener after initial installation, simply add artificial periodic regeneration salt, you can achieve continuous production of water in the automatic condition, save a lot of manpower and material resources.
2; large exchange capacity; low salt consumption
Commonly used manual equipment, capacity, two indicators of the level of salt consumption operational level staff directly affect the exchange automatic softener equipment by avoiding the influence of human factors to achieve a strict automatic control, it will generally work exchange capacity of the resin 1000 g eq / m 3, while the salt consumption may be less than 100 g / g equivalent.
3, low power consumption
Commonly used manual devices require at least one salt pump and often corrosion problems, maintenance workload is also a great direct impact on the safe and stable operation of the equipment, while the automatic equipment without salt pump, power consumption is low.
4; reliable performance; stable
Zhengzhou IndyMac from years of practical application point of view, automatic water softening equipment DM stable performance, sensitive and reliable, but also never been abnormal. Coupled with the company's design and rich experience, comprehensive service, more so that the device is in good working condition.